Midnite MNPV16HV DISCO 4X-PSB 16 String PV Combiner
|Item Number: MNS-43000|
|Last Price Update: 12/28/2021|
|Manufacturer: MidNite Solar|
|Made In: United States|
|Model Number: MNPV16HV DISCO 4X-PSB|
Midnite Rapid Shutdown 16 String PV Combiner PSB Disco Box
Midnite Solar 16 String Solar Combiner & All in 1 Disconnect Box With Power Supply Board for plug and play compatibility with the Midnite Solar Birdhouse System Controller - used for Rapid Shut Down Per NEC 690.12 in solar electric systems.
This box is made to combine strings of solar panels and also serve as a load break disconnect. Even remotely disconnect this box when used in conjunction with the Midnite Solar Birdhouse System Controller. You can use up to 16 circuits in and only 1 single Positive/Negative home run out of this box, or break the output in half to serve 2 totally separate MPPT inverter inputs or 2 separate charge controllers. As this box is NEMA-4R rated - it can be mounted in any location or outdoor environment and in almost any position - so mount this combiner within 10 feet of your solar array and you have met the NEC 690.12 Code Requirement for rapid solar array emergency shutdown!
The MNPV16HV DISCO 4X's red handled is LOCKABLE IN THE OFF POSITION!
Convertible configuration (field configurable)
Sixteen strings combined for up to 230 Amps single pole disconnect)
8 + 8 strings, separate PV+ and PV- for use with 2 inverters (2 pole 115A disconnect)
8 strings plus, 8 strings minus for use with non-isolated inverters (2 pole 115A 600VDC disconnect)
Disconnect switch has built in shunt trip with positive feedback
See thru dead-front & color coded busbar guards included
Optional PV connected power supply
Load Break Rated
Optional AC connected power supply for redundancy
Type 4X aluminum enclosure (no rust, won't turn to dust) conduit/strain relief holes punched
90 Degree C connections
Fuse-holders (MNTS) installed
15a/600v fuses installed
Meets 2014 NEC 690.12
Warranty - 5 yrs.
Listed by ETL for US & Canada
Made in the USA
One MNSPD-600 (Surge Protection Device)
Sixteen 1/2" strain reliefs (MNSR-1000)
Twenty-five 1/2" NUT MNT 14
Nine HOLE PLUG 1/2" NPT (MNHOLE PLUG 1/2)
Nine GASKET 1/2"
Two 10-32 X 7/8" SCREWS
Two 10-32 X 3/6" SCREWS
Two 3/8 16 X 7/8" BOLTS
Twelve 10-32 KEPS NUT
One TERMINAL PIN 18-22 AWG.
One TERMINAL PIN 10-12 AWG.
One WHITE INSULATOR
One BLUE WRENCH (MNWRENCH)
The difference between the regular Disco combiners and the DLTL version is that the MNPV16HV-Disco-4X is made for a single 16 string inverter, 2 8 sting inverters or one 8 string transformer-less whereas the DLTL is set up for 8 strings in and 2 strings out for Dual MPPT inverters or 2 separate solar charge controllers.